FRP Lining Service
|Surface Finishing||Color Coated|
Chemicals can be severely corrosive to above-ground metal storage tanks, resulting in possible leaks. The average corrosion rate of some carbon-steel storage tanks in certain services at ambient temperatures is more than 1 mil per year, with leaks developing in as few as five years. These leaks result in costs for repair and possible environmental penalties.corrosion sometimes increases when a layer of water containing soluble salts and chlorides settles to the bottom.These compounds are highly corrosive in themselves, and they can generate a strong electrolyte that further promotes corrosion from within. There can be a problem with external tank corrosion as well. The bottoms of above-ground storage tanks are susceptible to corrosion, especially if the tanks are close to salt water or subject to stray electrical currents in the soil.